Product Specifications. • 9th edition approved UL • Capacity of up to 64 panels with zones of programming through software. • Powerful and versatile . FireNET FN/FN UL/FM approved. Expandable loop and connect to other panel. ANALOG ADDRESS FIRE CONTL PAN, Hochiki. Description: Analog Address Fire Contl Panel; Category: Addressable Panels, Fire Control Panels, Fire; UPC.
Mostrando 19—36 de 90 resultados Orden predeterminado Ordenar por popularidad Ordenar por hochi,i Ordenar por precio: Post Thu Mar 02, Events are reported to a compatible central station monitoring receiver.
Any power consumed by devices connected to a SOM powered by the panel is also part of that 4 amps. The ones made by Hochiki are controlled and supervised by a NAC from the main panel. Sorry but I cannot give an exact answer to such a generic question. I am very beginner in fire detection system.
While studying the installation manual of firenet analog addressable system there are something confused me. That means 4 NACs at 1 amp each. Can i directly connect sounder base in a SLC loop?
From the Firenet installation manual: The device address is uniquely stored on an onboard. I know this is illegal.
NYC APPROVED FIRENET – TWO SLC
Also i know that will not supervised. The SOM provides a supervised 24VDC polarity reversing output on the SLC loop most commonly used for audible and visual signaling appliances or triggering a remote notification appliance circuit power expander.
Thanks for your reply. The current used by each NAC has to be added hofhiki and cannot exceed 4 amps total.
Компоненты и оборудование hochiki со склада и под заказ. Каталог продукции.
That means i 4 loop of NAC devices? All Rights Reserved This has to hochoki decided by knowing what is connected to each SOM, how much current is being used, and if that is in the capability of the power supply. According to the manual I downloaded there is an addressable manual station. Flexible Grooved Coupling – Series. But what i posted will it work or not?
Am i right or wrong please explain. Post Thu Mar 02, 1: In other words, there is no hard set limit. Post Mon Mar 20, User Control Panel Profile Logout. Post Mon Feb 27, 5: I don’t have any practical experience.
I do not know if it is acceptable fn-22127 your particular job site. They can be installed remotely in the building so wire distance and voltage drop issues are reduced.
Post Wed Mar 01, 1: Again, the amount of devices depends on the device’s rating, wire gauge, current draw of each device, etc Post Wed Mar 01, 7: You cannot just throw some relays and generic power supplies in the circuit. Post Sun Mar 19, 7: I know lots of experts are here. Then there should be a module to control Sprinklers system and a fn2127 should be sent to that module from a control panel to activate the Sprinklers.
But As far i know that when detectors detects then it passes a signal towards the panel and after a mentioned time panel pass a signal to NAC and NAC will generate power through the notification devices and alarm generate.
That means when detectors detects then all horns will sound automatically but not supervised. Up to devices can be hhochiki on a single SLC loop.